I have found a number of performance issues with AC23 that wern't there
in the RC version. 1. Adjusting heights or widths of complex profiles is
incredibly slow. Selecting a node to stretch cause a spinning ball for
10-15 seconds each time. If I over...
For some reason in the last 1 week some of my AC21 updated pln files
(these are legacy projects brought forward in many iterations of
ARCHICAD) won't load. AC21 crashes after loading a library that I have
warnings about being corrupted but have alway...
Please extend Graphic Overrides to include turning off layers and hiding
elements. By doing this it can completely replace the renovation filters
and allow us multiple configurations of model and plan options.
My heat loss / gain and hydronic design requirements are calculated
through a proprietary Excel workbook I created almost 20 years ago. I
tried setting up Archicad to produce schedules with measured values but
gave up. Using the measuring tool and CI...
This was probably the most complex I have done. 1:250 final scale I
received a .dxf from the surveyor and placed it on a storey well below
the bottom storey then used it as a ghost storey for a 3d Site Plan
storey (this is a template storey sitting b...
I've done many using polygon layouts first. Then I make any adjustments
(to match required lengths for heating output and spacing ) and magic
wand MEP pipe tool on the polygon. Make sure the pipe corners are set to
your desired radius. Then one that...
One way that I use for this type of situation is to move the pivot line
inward on all sides. You will need to calculate the amount to move by
using the pitch ratio x (the width of the room divided by 2) i.e. 5/12 x